The client’s existing poorly-designed system couldn’t maintain constant positive pressure within the production area to comply with BRC guidelines and low-level temperatures were high in summer months.
We discovered the existing fans had been applied incorrectly and, as the filters became soiled, the system pressure caused the fans to stall, resulting in an almost complete loss of air flow.
All of the supply air was delivered at a high level (7m), resulting in poor air distribution.
All supply grille boxes also suffered with very bad condensation, while the paint finish on these boxes was flaking off. The production area suffered from a bad combination of oil fumes (stemming from the frying process) as well as steam evident in the atmosphere.
The air distribution was changed from high-level, high-velocity grilles to low-level displacement, while all the grille boxes were upgraded to stainless displacement terminals.
Any grilles which were over the product were relocated to aisles. Fans were also modified to prevent stalling.
We found Penmann to have an excellent understanding not only of air conditioning and refrigeration but also of the production process and the logistics that surround it. All timescales were achieved and the systems are working well. I would have no hesitation in recommending Penmann to others.David Underdown, Sales Director, Rachels Dairy
The service you provide through Penmann is always thorough, thoughtful and designed for a duty and service level that reflects the demanding 24/7/364 days operation we run here, and we therefore always call you first when manufacturing problems need specialised and bespoke HVAC solutions.Robin Wright, Projects Manager, Bakkavor Desserts Newark
Arla was pleased to engage the services of a locally based company on such a prestigious project. Penmann were able to work seamlessly with us to deliver a high quality product.Tim Hutchinson, Project Manager, Arla Foods Stourton
We have worked with Penmann on projects across all our UK sites. Their attention to detail is evident throughout each project.
The phrase ‘Turnkey Solution’ is used extensively in projects, but never has it been better suited than for describing a project by Penmann.Tom Mitson, Lantmännen Unibake
We are very happy with the cooling tunnels designed and supplied by Penmann. All projects have been undertaken in an extremely efficient manner and have been delivered on time and on budget, and we have been particularly pleased with the performance of the tunnels.Stephen Graves Factory Engineering Manager, Müller Dairy
All installation work was performed on time and to a high standard. The installation team, ensured that they worked safely and that the safety of others around the working area was considered at all times.Michael Clifford, Engineering Manager, Britvic Soft Drinks